At 20 ° C / 60%r.h. = 20,0 kg/day
Air flow and pressure:
Dry air, free blowing : 320 m3/h
Dry air, nominal : 240 m3/t
Reg. air, nominal: 40 m3/t
External pressure, dry air (at 240 m3/h): 80Pa
External pressure, reg. air (at 40 m3/h): 120Pa
Control and signals
On- / Off- rotary switch (Auto - 0 - Man)
Ammeter to control the reg. air flow.
Operation time counter
Outside socket connector for Hygrostat
Rugged construction of stainless steel.
Easy access for service and repair
The process air moves through the continuously turning rotor. The rotor includes the moisture of air. A stream of air which flows into opposite direction is heated up by a PTC-heater. This hot air evaporates the water from the rotor and leaves the unit and the room as warm and wet reg.-air. Common fan for both streams.
The rotor is made of min. 82% Silicagel, which is laced chemically and not solvably to a base of glass fiber. An impregnation is not required. The regeneration temperature of the rotor is with approx. 120-140°C..
1 x 230 V / 50/60 Hz, connecting cable: 2 mtr. with Schuko coupler
PTC - heater: 920kW
Total consumtion: 1,060W
Installation and dimensions:
4 rubber dampers
Easy to carry with the handle on the top of the unit
Commn intake for process air and reg. air.
Dry air : Ø100mm connection (spiro).
Reg. air: Ø80mm connection (spiro)
Use of the unit:
Coupler into the socket. Turn on device on the rotary switch. Adjust the air volumes in accordance with operating manual and display on the ammeter. Lead regeneration exhaust hose (accessory) from the room.
length / width / height:, cabinet: 395 mm/ 330 mm/ 335 mm
length / width / height:, total: 475 mm/ 335 mm/ 360 mm
Change filter, check rotor belt